Organizations are beginning to recognize the importance of having a backup for their uninterruptible power supplies to protect critical information. As the use of N+1 configurations for a UPS system increases, it becomes important for organizations to select the best configuration to meet their needs. In addition to isolated redundant configuration and parallel redundant configuration, organizations also have the option of using an internally “modular” redundant configuration for their UPS system.
Visit Also: UPS Maintenance contract in Pakistan
An internally modular redundant configuration or setup uses only one battery for all UPS modules. If one of the modules is not functioning properly, the other modules act as a backup. This ensures that the equipment connected to the system continues to receive power. This configuration is the simplest type of N+1 UPS configuration. Apart from using only one battery, all UPS modules also share one output.
In this configuration, the load is shared among all modules. The capacity of this configuration can be increased by adding more modules. However, a major disadvantage of this configuration is the single battery that is used. If the battery fails, the system may not be able to provide the required power during a power outage. The battery may not function properly when it reaches its useful life.
An internally modular redundant configuration for a UPS system is an efficient way to protect critical enterprise equipment. It can be easily configured to operate close to its capacity. In this situation, a UPS system usually runs efficiently. For details, please visit: https://upsonlinestore.com/